The most common method of water disinfection and has been safely used for centuries. Excellent for potable water disinfection. Utilise either gas chlorine, sodium hypochlorite or calcium hypochlorite.
Chlorine is a gas at room temperature and pressure and is soluble in water. Chlorine hydrolyses with water to form hypochlorous acid and hydrochloric acid according to the following equation:
Cl2 + H2O → HOCl + HCl
Sodium Hypochlorite reacts with water as follows:
2NaOCl + H2O → NaOH + NaCl
This hydrolysis feature makes chlorine very suitable for water disinfection applications where turbulence is present, as chlorine is not present in water as a dissolved gas like chlorine dioxide or ozone.
Sodium hypochlorite is available as a 12.5% solution or 10% solution (depending upon location).
Calcium hypochlorite tablets and granules are sold in 10kg and 50kg buckets. The tablets and granules contain 65% available chlorine.
The key feature of the gas chlorination system for water disinfection is that it operates completely under vacuum and is therefore inherently safe. If the booster pump stops or the venturi becomes blocked or the vacuum tube is broken, vacuum is lost at the chlorinator. The inlet pressure reducing valve immediately closes and the cylinder or drum is completely isolated. Even if the cylinder was to fall over and the body of the chlorinator was to smash, the inlet pressure reducing valve would still stay closed and no chlorine gas would escape.
Gas chlorination can occur from 920kg drums. Chlorinators are equipped with a drop leg and heater where any liquid chlorine is vaporised. Normally, this is only required for connection of the drum immediately after transport. After a short operation time, the heater is not required but is normally left on.
Gas chlorination systems are usually supplied as duty-standby units so that chlorine gas is continuously available for water disinfection. Change-over from the duty cylinder or drum to the standby unit is via a vacuum shuttle valve. When the cylinder is empty, vacuum increases to such an extent that the valve shuttle is pulled over to the other side, allowing the standby cylinder to come on line.
12.5% sodium hypochlorite undergoes gasification as it decomposes to give off oxygen gas. This gasification can cause problems with chemical metering pumps as the gas will accumulate in the metering pump suction line, eventually making its way into the liquid end where loss of prime is the result. The ProMinent Gamma/L and Beta dosing pumps have solved this problem with the specially designed auto-degassing liquid end. Gas is removed from the suction line through a vent valve and directed back to the storage tank with a small amount of liquid. The clear chemical is then dosed through the discharge valve.
Larger metering pumps (>20 L/hr) don’t usually suffer from loss of prime as the valves are much larger and the volume of chemical being pumped is also larger.
Suction connections between the bulk sodium hypochlorite storage tank and the metering pump should be designed to minimise formation of gas pockets. A calibration cylinder immediately prior to the metering pump will function as a gas accumulator and allow gas to rise and vent off. If the suction line is run downwards from the tank to the pump, gas will rise back into the tank.
One way to prevent gasification is to dilute the 12.5% solution to 1% using potable water. Although the metering pump will have to be 12.5 times larger, the 1% solution will last decay approximately 144 times slower than the concentrated solution.
Definition of Strength
Five common definitions of sodium hypochlorite solution strength are as follows:
- Grams per litre of available chlorine = The weight of available chlorine in grams in 1L of sodium hypochlorite solution. This is determined by analysis.
- Grams per litre of sodium hypochlorite = 1.05 x grams per litre available chlorine.
- Trade percent available chlorine = grams per litre available chlorine/10
- Weight percent available chlorine = grams per litre available chlorine/ (10 x sg)
- Weight percent sodium hypochlorite = weight percent available chlorine x 1.05
Typical chlorine residual analysers are supplied on wall mount backboards, pre-wired and pre-plumbed. The controller will feedback control any system such as a gas chlorinator, dosing pump or cal hypo feeder.
Sodium Hypochlorite is a dangerous good and has the issue that a splash can cause blindness. Transfer of chemical from bulk tankers is to be done without operator intervention using appropriately designed systems. Transfer of small quantities (20L or 200L) can be done with a Dioxide chemical transfer system and there will be no operator contact.
Calcium hypochlorite tablets are not a major safety concern except that they should not be heated or put in contact with oxidisable substances
Please contact us for further information on chlorine water disinfection systems.